RPM Solutions developed a Center Distribution Plate-Intermediate (CDP-I)
and resolved the vibration issues experienced at a plant utilizing the
standard short version of this component.
The atomizer routinely experienced spikes in vibration at approximately
125 gallons per minute. In some cases, these vibration spikes would
trip the atomizer offline making the atomizer unreliable.
The graphs below illustrate the vibration readings experienced before and
after the CDP-I was installed. The CDP-I continues to operate at normal
conditions (50 to 200 gallons per minute) with minimum vibration variance.
The same results were experienced with the other atomizers at this plant.
The implementation of the CDP-I dramatically reduced the amount of atomizer trips
and made the operation of the plant’s atomizers consistent and reliable.
The Atomizer Monitoring System provides the tools to help you manage all aspects of
maintaining your Atomizers. Save Time. Save Money. Improve Safety. Find out how ...
Copyright © 2017 RPM Solutions, Inc. All Rights Reserved.
RPM Solutions, Inc.
333 Concourse Drive
Rapid City,SD 57703
e-mail: Sales (at) RPMSolutions (dot) com